This Equipment is designed for Wall Mounting
The unit must be located on
a flat surface:-
1. Remove the face panel via
the four screws located in the corners.
2. Drill the rear of the
case in a minimum of two places to suit the precise location of the
unit ensuring the cable gland is positioned at the bottom.
3. Use suitable screws to
affix to the desired location.
4. Pass all cables through
the cable gland and affix the green connector plugs as detailed
5. Plug the connectors into
the correct sockets on the rear of the face panel and relocated
using the four screws to fasten the face to the case.
Do not over tighten the corner screws.
Connect the controller using
the Green plugs provided as per the above wiring diagram making sure
the power supply is via a standard three pin 13 amp plug fitted with
a 13 amp fuse and a Residual Current Circuit Breaker. Pass all
cables through the cable gland by making a small slit with a sharp
The supplied cable gland must be used and be
located at the bottom of the unit.
Initial Setting and Configuration
This unit has been factory set to the following configuration with
the exception of the set point which was set at 85 degrees F for
testing purposes only. The controller is set to Heating mode. Read
out is in degrees Fahrenheit. Differential has been set at 1 degree
F. and the maximum allowable set point temperature has been
restricted to 100 degrees F.